With our five star reputation and professional education and experience, it's no wonder that Orland Park, IL chooses PDM as their plumber and heating and cooling expert.
Receive a proven 138 year track record of keeping your Orland Park home and business safe and comfortable! Your PDM Plumbing, Heating, Cooling service team offers professional analysis of your comfort needs and great advice to fit your lifestyle. For additional ease of mind, your PDM service is backed by a strong warranty.
You PDM Comfort Team strives to set industry-leading standards when it comes to plumbing, heating and air conditioning repair, maintenance and replacement. PDM offers solid advice at the right price. Enjoy the convenience of our financing options that make repairs, new equipment and accessories affordable.
- Heating Service in Orland Park, IL
- Air Conditioning Service in Orland Park, IL
- Indoor Air Quality Service in Orland Park, IL
- Duct Cleaning in Orland Park, IL
- Plumbing in Orland Park, IL
- Drain Cleaning in Orland Park, IL
- Water Heater Service in Orland Park, IL
- Water Backflow Device Testing in Orland Park, IL
We take great care to treat your home or business like it was our own. Any mess made will be cleaned up so you can get back to doing what you love quickly without hassle.
We love being Orland Park's, plumber and heating and cooling technician! Our exceptional 138 year reputation is the foundation for our success. To schedule plumbing, furnace, boiler, air conditioning repair or replacement for your Orland Park area home or business, call a trusted partner today!
for Orland Park, IL
Our Reviews by City
Cleaned and serviced condensing unit. Tested capacitor, contactor, fan motor amperage and compressor amperage. Everything tested in accurate working condition. Checked the refrigerant levels. The R410a refrigerant was in accurate efficiency range. Performed clean and check on furnace. Everything was in accurate working condition. Customer is ordering a new filter. He needs a April air 510. Customer signed and used maintenance program. Will renew in spring.
Cleaned and serviced both condensing units. Both units where very dirty and had to burn off cottonwood then hose them both out. Tested capacitors, contactors, fan motor amperages and compressor amperages. Everything was in accurate working condition. Both units have R410A refrigerant. Both were in accurate efficiency range.
AC repair. Faulty electrical. Customer stated the other day the unit popped the fuse when starting. They reswitched the fuse in the breaker. Then they were hearing a loud humming noise. The compressor was trying to start but could not. Installed the hard start kit with relay. Now compressor is starting right up and is in accurate working condition.
Service A/C for season, Service generator, cleaned screens ports on Lavatory faucet and laundry faucet.
Cleaned and serviced condensing unit. Condensing unit was 1 lbs low on r410a refrigerant.
Clean and inspect AC unit recommend replacing
Clean and inspect AC unit
Water leak. Open wall in laundry found no leak, installed access door, repipe above drop ceiling for laundry room. Clean, test and tune two furnaces.
Boiler repair. Replace zone valve.
Bathroom drain cleaning. Pulled toilet in hallway bathroom and successfully rodded.
Furnace repair. Customer had concerns about the volume of the inducer fan motor assembly. Performed final testing on new installation. No charge per technician.
Service hot water boiler, cleaned and tested furnace and found some ignition faults, replaced HSI, sensor.
Clean and check furnace system. This is the second visit on this plan.
Furnace maintenance for the season.
Service, tune-up furnace for the season, set up annual service plan. Replaced humidifier pad. Toilet loose, tighten toilet and caulked base. Service back up generator for the year.
Air conditioning repair. Electrical fault, install hard start kit on outdoor air conditioning unit. Check AC refrigerant charge, removed 1-1/4 Ibs. This is his ac clean done. Clean and check furnace. Service plan start date today. Material in notes
ESTIMATE FOR A NEW ENERGY EFFICIENT CENTRAL AIR CONDITIONING UNIT AND INDOOR AIR CLEANER.
Air conditioning system has leak in coil. Installed new evaporator coil, removed Freon, brazed new coil connections, pulled vacuum on system and charge to correct pressures.
Air conditioning repair. No A/ C, reconnected low voltage on outdoor unit, Cleaned, tuned AC system. Provide estimate on 2nd discharge pipe for sump pump.
Replace high efficiency furnace and air conditioning system quote.
Faucet repair. Tighten packing nut.
Air conditioning repair. Customer states that second-floor AC system is not working properly. Found electrical fault to condenser. Rewired furnace board. Reconnected and tested. AC is cooling now.
Program back up generator. Replace HVAC fan motor and blade and add a switch closer to the attic door.
Air conditioning repair and maintenance service call. Clean and checked air conditioning systems. This is the second visit on these annual HVAC service plans. No air conditioning call for second floor unit. Found electrical fault. Replaced run capacitor, 45/5. Added starting capacitor. Second floor system very dirty with cottonwood fibers.
Bathroom drain cleaning. Pull toilet, power rod drain line to clear blockage. Reset new power assisted toilet, test for leaks. New toilet seat, two wax rings.