The Leader In Lockport, IL Plumbing, Heating & Air Conditioning Service Since 1885
Since 1885, PDM Plumbing, Heating & Cooling has served the good people of Lockport, IL for all of their plumbing and HVAC needs. How many companies do you know that can claim to have experience that spans three centuries? In that time, we've built a solid reputation as contracting experts who can handle any job with exceptional service and quality workmanship. Our team offers you the perfect mix of knowledge, authority and most importantly - trust. Your great-grandparents trusted us. Your grandparents trusted us. You can count on us, too.
Put Your Trust In Our Team For Your HVAC & Plumbing Services in Lockport, IL
It's not enough to be good at what we do. We want our customers to know they can trust us with their home and equipment. Besides extensive training and experience, all of our technicians have passed thorough background checks and substance abuse testing. We only hire the best, because you deserve the best. When your work is done, you'll scarcely know we were there.
The Proof Is Out There
We value our customers above all else - and with them, their opinions. Their testimonies are paramount to our success. That's why we invite you to read what some of your Lockport, IL neighbors have to say about the service they've received from PDM. To schedule your plumbing, heating or air conditioning service, send us a message online or call 815-726-6264 today!
Yes, HVAC systems need to be serviced in Lockport, IL. Having your HVAC system serviced ensures that:
- Your HVAC system is covered under warranty
- Your HVAC system lasts longer
- Your HVAC system runs more efficiently
It is recommended that you have your HVAC system serviced twice a year. When your HVAC unit is maintained frequently, you spend less on energy bills each month and your HVAC system breaks down less often. To get your HVAC system serviced, contact us today.
You should replace your HVAC system in Lockport, IL every 10-15 years. Most HVAC systems begin to break down after 10-15 years, but the service life of your unit can greatly depend on how often it is maintenanced. A well maintained HVAC system will last longer and run smoother. However, if you do not have your HVAC unit regularly maintenanced, your HVAC system may not last its full life expectancy. To get your HVAC system replaced, contact us today.
A plumber typically costs around $150-$350 in Lockport, IL. However, the price can fluctuate depending on the type of service. Having a clog removed from a drain or a leaky faucet fixed will be fairly inexpensive. Although, sewage issues and broken pipes can be costly to repair and replace. Regardless of the plumbing problem you are experiencing, you should have it addressed quickly to protect the safety of your family and your home. To get your plumbing inspected or repaired, contact us today.
A few reasons you may want to replace your water heater rather than repair it in Lockport, IL include:
- Your water heater is over 10 years old
- Your water heater has a tank leak
- The cost to repair it outweighs the cost to replace it
Another reason you should replace your water heater is if your energy bills have increased. Replacing an old or inefficient water heater with a new water heater will save you more on energy and repairs in the long run. To get your water heater repaired or replaced, contact us today.
for Lockport, IL
Our Reviews by City
Clean and check furnace system. Renewed customer service agreement. This is the first visit on this new plan. Replaced customer supplied humidifier pad. Lowered water flow to humidifier.
Bathroom remodel. Replace 2 toilets one in 1st floor hall bath, ice grey elongated, second toilet in master bath white elongated. Also replace 3 faucets, two in master bath and one in hall bath Moen Branford wide spread with rough in valves brushed nickel, **** for the master bathroom sinks their are no matches for that size and color, counter top would have to be replaced.
Faucet repair. Replaced Moen posi temp cartridge.
Furnace repair. No heat call. Found electrical faultI. Replaced HSI and tested.
School drain cleaning. Vacuumed water out of mop sink drain in lower level janitor closet near men’s locker room. Found trap rotted out and needs to be dug up to repair.
Toilet leaking. Pull and reset toilet.
Toilet leaking. Pull and reset toilet.
Furnace repair. Customer stated that the temperature was swinging up and down. Performed a clean and check on furnace and determined no issues at this time. If issues persist, recommend dealing/replacing the thermostat.
Steam boiler service
Water piping repair. Repiped water to powder room toilet with new angle stop. Rebuilt Delta shower faucet in master bath. Replaced outside lawn faucet on east side of house. Replaced saddle valve for ice maker with angle stop. Flushed and chlorinated water heater.
Clean and check to furnace systems. Replaced customer supplied humidifier pad. This is the second visit on this plan.
Clean and check furnace system. Renewed customer service agreement. This is the first visit on this new plan. Replaced customer supply filter, checked humidifier pad good. Replaced run capacitor.
Commercial drain cleaning. Pulled urinal and Rodded drain line. Repair urinal. Rebuilt vacuum breaker and changed diaphragm in flush valve. Flush valve is pretty corroded and leaking from stop, suggest replacement of flush valve including new stop. (.5 gpf)
Sump pump repair. Disconnected sump line from sewer and ran it out the side of the house.
Clean and check furnace. Rusty water I flushed water softener line regenerate softener. Drain cleaning. Rod sewer sewer goes out back clean out by wall / patio. 2nd CO by bush on corner of house this is where I open sewer. Tree roots blocked sewer line. Rod got stuck coming out recommended camera and locate.
Replaced 50 gallon power vent water heater.
Replaced kitchen faucet.
No heat call. This is the first time that we are looking at the HVAC system for this customer. Found numerous issues with system. First old humidifier hanging off the back, removed. No filter rack/filter in the system. Found return restriction inside ductwork Approximately 10“ x 10“. System has 100,000/5 ton Drive, Too big for the house/ductwork. Reduced gas pressure and increased fan speed. 53 degrees split 35/65 range. Main problem was the vacuum orifice was clogged. Performed clean and check on furnace system. Signed customer up for a service agreement. This is the first visit on this plan.
Winter maintenance visit. Clean, test and tune one Goodman and one Tempter furnace. Reset to factory specs. Replace 2- #201 furnace air filters and 2- #35 humidifier pads. Water heater check and flush tank to remove sediments. Inspect sump pumps and lift station pumps, one battery back up sump pump system operation, wall shelf is pulled off wall, re-anchor to wall. Sump pumps are working as of this date. Misc charge is re anchoring wall shelf. Material in notes.
Cc furnace, replace handle on toilet , fill valve with 9” supply line and flapper, used the more expensive handle and the fill valve flapper combo kit everything else is going to truck stock
Replaced sump pump with option 2 pump.
Annual boiler maintenance.
No heat call. Upon arrival found no high voltage at furnace. Disconnect at fuse panel was loose. Clean, test and tune furnace system Renewed customer annual service agreement.