With our five star reputation and professional education and experience, it's no wonder that Morris, IL chooses PDM as their plumbing, heating and cooling expert.
Our Morris plumbers and HVAC technicians are highly trained professionals with genuinely good hearts and great personalities. We can't wait to start the day! Need more convincing? Give us a try, and you'll see why! Call PDM for guaranteed service.
for Morris, IL
Our Reviews by City
Bathroom plumbing repair. Replace lavatory faucet and drain, replace tub pop up and over flow plate.
Water heater repair. Pulled gas burner to locate and clean 3 flame sensors. Hot water is flowing now.
Cleaned and serviced all 7 condensing units. Tested all capacitors, contactors, and fan motor amperages. Also checked all refrigerant levels. The conclusions of units as followed. Unit #1 alley- added 1lbs of R410a refrigerant. Capacitor,contactor, and fan Motor were in accurate working condition. Unit #2 alley- added 1-1/2 lbs of R410a refrigerant. Capacitor,contactor,and fan motor were in accurate working condition. Unit #3alley- replaced a single run capacitor 12.5mrf. Contactor and fan motor Amperage were in accurate working condition. The refrigerant levels were accurate. Unit #1 rooftop- added 2lbs of R410a refrigerant. Capacitor,contactor and fan motor amperage were all in accurate working condition. Unit #2 rooftop- Added 1lbs of R410a refrigerant. Capacitor,contactor,and fan motor ampera
Air chamber for laundry box froze and split, cut out piping and repaired air chamber with coupling. Then put piping back in.
Furnace humidifier repair. Angle stop for humidifier was leaking. Replace shut off valve.
ESTIMATE FOR NEW COMMERCIAL HVAC UNIT.
ESTIMATE FOR A NEW A/C UNIT.
Furnace repair. Replaced exhaust piping of furnace.
ESTIMATE TO MOVE AC WHILE DECK IS INSTALLED AND THEN PUT IT BACK 9-11
Furnace maintenance. Clean and check 7 furnace systems. Replaced customer supplied filters as needed. Replace 3 inch pvc that is leaking.
White Oak area home water heater leaking. Replaced 40 gallon water heater with energy efficient Bradford White gas water heater. Test for safe operation. Recycle old tank.
FURNISH LABOR AND MATERIAL FOR THE INSTALLATION OF A COMMERCIAL HOT WATER HEATER AS FOLLOWS: -CLOSE ISOLATION VALVE TO HOT WATER HEATER -DRAIN DOWN HOT WATER HEATER -DISCONNECT UTILITIES TO HEATER -REMOVAL AND DISPOSAL OF HEATER FROM PREMISES -INSTALL NEW AO SMITH BTH 199 100 GALLON COMMERCIAL HOT WATER HEATER -CONNECTIONS TO EXISTING HOT AND COLD WATER PIPING -CONNECTIONS TO EXISTING GAS AND ELECTRIC -CONNECTIONS TO EXISTING PVC VENT AND INTAKE PIPING -INSTALL NEW THERMAL EXPANSION TANK -REFILL SYSTEM WITH WATER -START UP AND TEST OPERATION -WORK TO BE DONE DURING NORMAL WORKING HOURS
Furnace repair. No heat call. Very dirty flame sensor. Propane. Clean and check furnace system for safe, efficient operation.
Commercial HVAC service. Inspected and tuned air conditioning systems for the whole building. Seven units total. Three units in alley and four units on the roof. All 5 ton condensers cooling normally.
Morris air conditioning check-up. Reset AC system to factory specs for safe, efficient operation. Running well.
Boiler repair on infloor heating system and stat replacement
Urinal leaking on 3rd floor. Remove urinal and replace fitting in wall. Rehang urinal, test operation nd clean up.