With our five star reputation and professional education and experience, it's no wonder that Manhattan, IL chooses PDM as their plumber and heating and cooling expert. Our Manhattan plumbers and HVAC technicians are highly trained professionals with genuinely good hearts and great personalities.
Receive a proven 136 year track record of keeping your Manhattan home and business safe and comfortable! Your PDM Plumbing, Heating, Cooling service team offers professional analysis of your comfort needs and great advice to fit your lifestyle.
- Heating Service in Manhattan, IL
- Air Conditioning Service in Manhattan, IL
- Indoor Air Quality Service in Manhattan, IL
- Duct Cleaning in Manhattan, IL
- Plumbing in Manhattan, IL
- Drain Cleaning in Manhattan, IL
- Water Heater Service in Manhattan, IL
- Water Backflow Device Testing in Manhattan, IL
We take great care to treat your home or business like it was our own. Any mess made will be cleaned up so you can get back to doing what you love quickly without hassle.
Need more convincing? Give us a try, and you'll see why! Call PDM for guaranteed service.
for Manhattan, IL
Our Reviews by City
Furnace repair. Inspected unit. Found flame sensor dirty, cleaned and retested.
Clean and check furnace system. Renewed customer service agreement. This is the first visit on this new plan.
Water heater repair. Replace old expansion tank and replace old relief valve 30 psi, expansion tank had 7 year manufacturing warranty.
Clean and check furnace system. Found an electrical fault, decreased gas pressure and increased fan speed. Renew customer dual anservice agreement. Checked water heater, not getting enough hot water per customer. Increased water temperature.
Service Hot water boiler
Cc furnace no issues at time of inspection, replace customer supplied garbage disposal
Heating system maintenance. Service 2 furnaces and small in-floor boiler systems, set up annual service agreement plans. Maintenance for tankless hot water heater, direct vent.
Water heater service. Investigated water heater and area around it but couldn’t find the source of where the water was coming from, customer last saw it pooling a few days ago. Recommend keeping an eye on it and calling back if it shows up again.
Toilet repair. Toilet is not flushing properly. Found Mansfield flush valve seal worn and dislodged, replaced seal. Tested.
Service A/C for season
Bathroom plumbing repair. Replaced lavatory faucet.
Clean and check air conditioning system. This is the second visit on this annual HVAC service plan.
Plumbing repair. Outdoor lawn faucet replaced and sump pump piping repair.
Estimate on hot water upgrade to a tankless water heater.
Yard faucet repair. Vacuum breaker for Mansfield outside lawn faucet in front of the house broken, unable to access the back of the faucet due to cabinetry in the kitchen needing to be removed. Pulled the vacuum breaker off of a scrap faucet that I had in the truck get him by for now.
Water heater repair. Replaced relief valve.
Boiler repair, not working, Performed system diagnosis and found faulty flue thermostatic fuse. Replaced and tested for safe operation.
Furnace repair. Clean and test furnace system. Replaced special order pressure switch, an automatic safety that shuts the furnace down if it senses negative pressure created by the draft inducer motor. This protects your home from exhaust fumes being reintroduced into the system. Furnace is running safely.
Plumbing repair. Found water pipe split at well tank. Replace section of pipe and fittings also reinstall laundry tub drain on lift station.
Ranch Oaks subdivision area hot water boiler repair. Rebled boiler system and flushed out fill valve.
Plumbing repair. Replaced kitchen faucet, repipe laundry drain. Replaced lawn faucet, replaced washing machine shut off valve. Furnace maintenance. Cleaned and tested furnace for safe, efficient operation.
Leighlinbridge subdivision home bathroom plumbing repair. Install 2 customer supplied lavatory faucets + pop up drains and 1 shower trim. Faucet repair, replace Moen cartridge in master bathroom.
Ran a bunch of water, could not get anything to back up. Found powder room toilet running, replaced flush valve seal (Kohler)
ESTIMATE TO INSTALL NEW GAS LINE AND POOL HEATER.
Clean and check furnace system. Renewed service agreement. Switched fan speeds heat to high, cool to med high.