With our five star reputation and professional education and experience, it's no wonder that Manhattan, IL chooses PDM as their plumber and heating and cooling expert. Our Manhattan plumbers and HVAC technicians are highly trained professionals with genuinely good hearts and great personalities.
Receive a proven 136 year track record of keeping your Manhattan home and business safe and comfortable! Your PDM Plumbing, Heating, Cooling service team offers professional analysis of your comfort needs and great advice to fit your lifestyle.
- Heating Service in Manhattan, IL
- Air Conditioning Service in Manhattan, IL
- Indoor Air Quality Service in Manhattan, IL
- Duct Cleaning in Manhattan, IL
- Plumbing in Manhattan, IL
- Drain Cleaning in Manhattan, IL
- Water Heater Service in Manhattan, IL
- Water Backflow Device Testing in Manhattan, IL
We take great care to treat your home or business like it was our own. Any mess made will be cleaned up so you can get back to doing what you love quickly without hassle.
Need more convincing? Give us a try, and you'll see why! Call PDM for guaranteed service.
for Manhattan, IL
Our Reviews by City
Rubber coupling on pair of pumps became detached because sump line outside froze because it was run above ground. Reattached pump to discharge line, ran 10’ of pvc outside for a temporary fix.
Furnace repair. Tested flame sensor, pressure switches, hsi, fan motor amperage and capacitor, inducer motor amperage, and gas valve voltage. Found furnace locked on flame sensor, cleaned sensor, furnace ignites and is working. Reset to factory specs for safe, efficient operation. Let customer know about our annul VIP maintenance agreement. And he would get 2 check ups a year one on ac unit and one on furnace. He will call in the spring to sign up for plan.
Cleaned and serviced furnace. Tested flame sensor, pressure switch , inducer motor amperage, fan motor amperage and capacitor, and gas valve voltage. Replaced humidifier pad (35) that customer provided. Furnace filter was just changed by customer. Everything is working as it should at this moment. Customer renewed maintenance program and will have both visits for spring and this coming fall. Gave customer estimates for new furnace/humidifier due to rust build up and furnace from 2004.
FURNISH LABOR AND MATERIAL FOR THE PLUMBING REPAIRS AS LISTED
Replaced customer supplied battery’s.
Water leak. Went up in the attic, found evidence of water staining on 6 inch flue pipe through the roof. Could not see any evidence of plumbing leakage through ceiling in laundry room. believe this is a roof flashing issue.
No heat call. Started with clean and diagnosing of furnace. Customer wanted to join maintenance member plan. After diagnosing, found high limit switch was failed to the open position. The furnace filter was extremely dirty and clogged up, thus making the high limit fail. Also tested flame sensor, pressure switches, hsi, fan motor amperage and capacitor, and inducer motor amperage. Replaced the high limit switch and hsi due to corrosion. Everything else was in adequate working condition. One visit on plan was used today and customer has one remaining for spring for condensing unit. Performed free inspection.
Cleaned and diagnosed furnace. Tested flame sensor, pressure switches, hsi, fan motor amperage and capacitor, and inducer motor. Everything is in accurate working condition however furnace in old being from 2005. Has rusty burners and inducer. Gave customer estimates for new furnace and he is considering next year. He did not want to do plan at this time.
Cleaned and serviced furnace. Tested flame sensor, pressure switches, hsi, fan motor amperage and capacitor, and inducer motor. Everything tested in accurate working. Gave customer estimate for new inducer motor due to slight winding noise that’s it’s producing. Customer has one visit remaining on our VIP service plan for spring.
Cleaned and serviced furnace. Tested flame sensor, pressure switches,hsi, fan motor amperage and capacitor. Flame sensor and hsi were replaced due to corrosion. Everything else tested in accurate working condition. Cleaned out exhaust pipe and blew out drain line. Customer Renewed maintenance program.
Inspected boiler for season.
Replaced water softener, found leak from pinched seal between head and tank, adapter, contacted Mid-America. They are working on getting the part. Returned to complete install and test.
Replace tankless water heater never run out of hot water. Test operation and clean up.
Installing new Tankless water heater
Test and certified 1- 1” RPZ backflow file report with city per state code.
Installed customer supplied well tank
Service A/C, condensation inside of furnace, blower motor must have stopped working. Everything working at this time. Suggest replacement of system, A/C is 14 years old and furnace is original. Send estimate.
Condensing unit not keeping up. Tested capacitor,contactor and fan mot amperages. Everything was in accurate acceptable levels. Unit was completely dirty however and very low on refrigerant. Hosed condensing coils out and added 2lbs of R410a refrigerant to achieve accurate efficiency levels.
ESTIMATE TO TEST AND CERTIFY (1) 1 INCH RPZ. LOCK BOX CODE 1970
Found gap in trim for tub valve, checked other possible leak sources, filled gap with silicone and suggested valve replacement.
Toilet leak repair. Pull and reset toilet, new rubber flange.
Sump pump service. Replaced main sump pump and battery backup with pair of sump pumps.
Sump pump repair. Main sump pump float doesn’t turn off, need to replace pump. Replaced pump.
Sump pump inspection. Tested sump pump, both primary and backup seem to be working fine. Told customer a new pump is $750.
Need to acquire parts for Mansfield toilet and return tomorrow at 10:30. On 3/9/23 returned and successfully repaired toilet.