Installation, Maintenance, Repair, and Replacement Since 1885.
With our five star reputation and professional education and experience, it’s no wonder that Rockdale, IL chooses PDM as their trusted plumbing, heating and cooling expert.
Our Rockdale plumbers and HVAC technicians are highly trained professionals with genuinely good hearts and great personalities. We’ll optimize the performance of your indoor comfort equipment!
- Plumbing repair in Rockdale
- Water heater repair in Rockdale
- Rockdale sump pumps
- Drain cleaning in Rockdale
- Rockdale Air conditioning repair
- Rockdale Furnace or boiler service
- Air purifier for easier breathing
- Whole home humidifier comfort
We take great care to treat your home or business like it was our own. Any mess made will be cleaned up so you can get back to doing what you love quickly without hassle. Need more convincing? Give us a try, and you’ll see why! Call PDM for guaranteed service.
for Rockdale, IL
Our Reviews by City
Very good service , Pete was a very nice tech , friendly and very nice to do business with , I will for sure reccomend him and PDM to others
James - Rockdale, IL
Great service , and price was very fair
Response from PDM Plumbing, Heating, Cooling Since 1885:
Well James, that was a very good review. Happy to hear Pete took good care of you. Thanks for sharing your review and trusting PDM. And thanks for referring friends and family! Stay dafe.
INSTALL NEW COMMERCIAL HVAC ROOFTOP UNITS. SET TO FACTORY SPECS, TEST FOR SAFE OPERATIONS. CLEAN UP WORK AREA.
Air conditioning repair. Customer complained of upstairs unit not cooling. Found 50 amp fuse blown, condenser coil very dirty, air filters recently replaced. Replaced with 60 amp fuse, cleaned condenser and tested. 28.4 degrees split. 7.5 ton unit, 3phase
Water backfow device testing. Found older RPZ with relief valve stuck open, parts were not immediately available to purchase so we went with a new RPZ watts LF009M2QT 1 inch with a new 1 inch strainer and piped relief drain to floor drain in room with a air gap to code. After install tested RPZ device passed inspection.
Commercial air conditioning repair. Responding to no air conditioning call for all three units on the west side of the building. West center unit- found condenser fan motor seized up. Installed and tested. West north unit - found system had VFD error code, reset. Working fine. Voltage 243 (x3). West south unit - working the whole time. (Probably because other two units were not working.
Commercial plumbing repair. RO system showing problem with low pressure switch. Inspected filter, it was a little dirty, try system with no pre filter. System still locking out on pressure. Reinstall filter and try with water softener in by-pass. Still has problems Pulled wye strainer before backflow device and found it full of rust sediment. I blew out wye strainer real good and tried system. RO system is working. Water softener ran through backwash. Ordered more reverse osmosis water filters so they have them on site.
Hot water heater repair. Egg smell from hot water heater, found anode rod deteriorated. Removed rod, chlorinate and flush water heater system. Fresh hot water now.
Estimate to install new reverse osmosis water filtering system. Reverse osmosis (RO) is the most economical method of removing 90% to 99% of all water contaminants.
Warehouse plumbing repair. Clogged main drain. Drain cleaning with power rod opened blockage. Sump pump maintenance.
Air conditioning clean, check and tune-up. Reset AC to factory specification for optimum performance. AC system is operating well.
Commercial backflow test. Test five water backflow devices. 1-4 inch , 2 - 1 1/2 inch , 1- 1 inch , 1 - 3/4 inch. All backflow devices are certified to be operating safely today.
Air conditioning service. Provide annual safety inspection and energy boosting AC tune up. AC unit tested and performing well for cool indoor temperatures.
Central air conditioner blowing warm air. Inspected and found the evaporator coil and blower wheel was dirty. Clean system and tune-up ac unit. AC is blowing cold air now. Customer is happy.
Air conditioning not working. Found pex tubing on drains. AC unit not leveled. Found 1inch of water in Duct work. AC pan on the A coil full of water and not draining the pan under unit full of water. Had to cut out all drain lines level unit and safety pan under unit run new 3/4 pvc drain line over to vent on drinking fountain to drain unit. Had to remove duct on the supply empty water dry out and insulate the inside of duct work. I also installed a deflector inside of duct so if unit blows water off of a coil it runs back into unit to the drain pan.
Gas leak tagged by Nicor Gas. Replaced section of gas piping and fittings, tested with air, found another leak, repaired and retested. Tested at 20psi for 20 minutes. Gas leak fixed.
Drain cleaning. Floor drains were backing up in kitchen, rodded from clean out after grease trap. Drains are now flowing normally.
Replace kitchen faucet in prep area, re-pipe 3 basin sink. Commercial rooftop HVAC units annual maintenance.
Restaurant water heater leaking. Replace AO Smith commercial hot water heater.
Heating repair. Furnace blower motor out on fault, will order relay and rewire control. Replaced motor relay on HVAC unit. NC.
Rockdale drain cleaning. Rod clogged floor drain in basement, observe water going down making sure not to re-plug.
Rockdale drain cleaning. Rod dishwasher line, cleared clog. Cleaned up.
Replace unit heater in rear of front building with modine 150k btu unit. PIP
Found furnace cycling on and off burners dirty and a dirty flame rod c/c furnace. Draft inducer has a hmmmm suggest it be replaced 641.00 Goodman furnace Model GMT070-3 Serial 010960775 20 years old 70,000input 56,000 output Replacement Champion furnace 80,000 input 80% single stage 3,401.00 80,000 input 80% 2 stage 3,892.00 Parts are in notes Paid by master card
ESTIMATE FOR NEW LP UNIT IN BACK OF BUILDING $5295.00
Hot water heater is leaking and needs replacement.
Rooftop furnace repair. Dealt with low heat, no heat issues on three units. No materials just time. To be billed. Recommend replacing gas valve on northwest RTU. Sent a customer a quote for a new gas valve.