Installation, Maintenance, Repair, and Replacement Since 1885.
With our five star reputation and professional education and experience, it's no wonder that Rockdale, IL chooses PDM as their trusted plumbing, heating and cooling expert.
Our Rockdale plumbers and HVAC technicians are highly trained professionals with genuinely good hearts and great personalities. We’ll optimize the performance of your indoor comfort equipment!
- Plumbing repair in Rockdale
- Water heater repair in Rockdale
- Rockdale sump pumps
- Drain cleaning in Rockdale
- Rockdale Air conditioning repair
- Rockdale Furnace or boiler service
- Air purifier for easier breathing
- Whole home humidifier comfort
We take great care to treat your home or business like it was our own. Any mess made will be cleaned up so you can get back to doing what you love quickly without hassle. Need more convincing? Give us a try, and you'll see why! Call PDM for guaranteed services.
for Rockdale, IL
Our Reviews by City
Estimate to replace furnace
RPZ water backflow preventer repair. Cleaned screen in strainer before rpz, replaced pre filters with customer supplied parts. Checked power at low pressure switch and unit kicked on.
Commercial water filtering repair. Check Reverse Osmosis system. Replace membrane customer supplied. Motor needs to be replaced and pump. Install new motor and pump on RO system, start system up. I have better pressure on the system with new pump and motor Before running at 45 PSI after with new pump/ motor 105 PSi on system marked gauge for future reference point.
Commercial drain cleaning. Rod slop sink in break room thru trap.
Rodded from clean out in women’s restroom by the bar.
Found water heater leaking. Replaced water heater under warranty.
Condensate pump repair. Run new discharge line in attic, replaced line in attic. Replaced pump.
Service 4 commercial furnaces, replaced all filters. Found fault with blower and replaced limit switch on banquet room unit.
Service furnace, humidifier.
Restaurant drain cleaning. Rodded grease trap discharge and drain line.
B&G pump service. Check water for air lock, all is good,
Commercial restaurant plumbing repair. Replace drain clean out plug in wall. Urinal issue was resolved by opening up the stop. Sink drain was leaking, replaced two slip joint nuts to stop leak.
Restaurant plumbing repair. Replace faucet on sink in employees kitchen bathroom. Replace drain assembly and p trap on this sink. Also hot water is set very hot, advised to install a mixing valve under this sink so employees do not get burned when used.
Commercial HVAC maintenance. Washed out 4 Champion Roof Top Units coils full of cotton wood. Reset units to factory specs. Replace all air filters in RTU. Washed air conditioner unit for bar on roof, evcon unit replace filter in unit up in ceiling bar hallway. Added 4lbs of 410a refrigerant in front AC unit, was really low.
Home central air conditioning repair. No air conditioning call. Found capacitor blown. AC capacitor supplies and stores energy. It has the ability or ‘capacity’ to save energy in the form of an electrical charge. When your thermostat tells your air conditioner to cool the house, the capacitor’s job is to provide two hundred forty volts to start up the compressor, fan motor, and blower motor. After the capacitor jumpstarts those parts, your A/C can begin cooling outside air and blowing it throughout your home. As your air conditioner is running, the capacitor collects and stores energy, similar to a rechargeable battery. Each time your air conditioner turns on, the capacitor provides a new blast of energy. Depending on your air conditioning unit, it may have multiple capacitors. Perform clean and check on cooling system. A new customer annual HVAC service agreement.
Service A/C for season. Clean, test and tune-up for safe, efficient air conditioning.
Commercial RPZ water backflow preventer certified test for 5 devices.
Commercial restaurant water heater repair. Leak on water heater piping. I replaced copper fittings and a section of 1 inch copper pipe. When I turned a heater pilot lite but main valve did not open check for voltage there is 24 volts at valve gas valve must have got wet it needed to be replaced. Install new gas valve and water heater is working. Also Don said no hot water at pre-rinse sink and hand sink, there is hot water now they had no hot water do to the heater gas valve not working. I also put a grey plastic tray over gas valve to protect it from water. Material in notes
Commercial restaurant kitchen plumbing repair. Install customer supplied sprayer with new hose and spring on pre rinse sink. Also repaired soap dispenser which was spraying water out of connection.
Restaurant drain cleaning. Successfully power rodded sewer from wall cleanout in women washroom.
Annual RPZ water backflow device test. Certified three water backflow devices.
Commercial boiler repair. Look at boiler system, system kept getting air locked. Turned boiler temperature down to 180*. 3 returns used temperature Gun to balance returns; one is fully open, 2nd return is 1/2 open and the 3rd one is 1/3 way open to balance system so the 3 zones heat even. Check for air in system. Recommend installing boiler air scoop on supply with auto vent. The back of church should have auto vent installed where it jumps below floor. Also may want to install auto vents back in Sanctuary with 1/4 ball valves. May want to install Tekmar controller on system to adjust water temp.
Drain cleaning. Removed basement toilet, Rodded sewer, reinstall toilet, tested.
Commercial drain repair. Replace floor drain, p- trap and floor drain assembly in women's washroom. Remove drain fountain by washrooms. Cap off center toilet in women's washroom. Rough-in toilet to ADA height in women's washroom.
Commercial plumbing repair. Replaced 1" ball valve for sprinkler system. complete rebuild of Zurn Wilkins 4 in. backflow device on fire system. Water backflow device tested, passed.