You PDM Comfort Team strives to set industry-leading standards when it comes to plumbing, heating and air conditioning repair, maintenance and replacement. PDM offers solid advice at the right price. Enjoy the convenience of our financing options that make repairs, new equipment and accessories affordable. Give us a try, and you'll see why!
- Heating Service in Naperville, IL
- Air Conditioning Service in Naperville, IL
- Plumbing in Naperville, IL
- Drain Cleaning in Naperville, IL
- Back-Up Generator Installation in Naperville, IL
- Remodeling Service in Naperville, IL
- Indoor Air Quality Service in Naperville, IL
- Duct Cleaning in Naperville, IL
As homeowners ourselves, we take great care to treat your home or business like it was our own. Any mess made will be cleaned up so you can get back to doing what you love quickly without hassle.
To schedule Naperville plumbing, furnace, boiler, air conditioning repair or replacement for your home or business, call a trusted partner today! Call 815-726-6264.
for Naperville, IL
Our Reviews by City
Cleaned and serviced condensing unit. Tested capacitor, contactor, and fan motor amperage and everything was in accurate working condition. Tested r410a refrigerant levels, and those too were in accurate range. Everything is working greatly. Customer wants to renew maintenance program.
Leak search with nitro to 450 psi, used bubbles found no leaks held for 30 minutes, pulled vac down to 500 micron added 4.3 #r410a, replaced capacitor 40+5
AC maintenance. Unit low on refrigerant, customer want to replace air conditioning unit.
Water leak in the Brown house and clogging the sink lines. Found the water softener to be in bypass mode, programmed timer and hardness into sofetner and put back into service. Ran through regeneration and also performed hardness test on well - 35 grains of hardness. If problems with water persist I recommend chlorinating the well and replacing the water softener
Water heater leaking, needs to be replaced. Replaced water heater
Heating repair. Low heat call out. Customer stated that thermostat said that it had been running for two hours. Upon detailed inspection found the pressure switch to be intermittent. Vacuum started at -1.30 then reduced to -1.00. Pressure switch at -.60. Replaced pressure switch and hose.
Clean and check furnace system. Renewed customer service agreement. This is the first visit on this new plan. 20 cent part from truck inventory
Clean, test and reset furnace to factory specs for safe, efficient operation.
Clean and check air conditioning system. This is the second visit on this annual HVAC service plan.
Central air conditioning maintenance. Clean, check ac operation. Reset to factory specs for safe, efficient operation.
Heating furnace repair. No heat call. Customer said air filter was very dirty because of remodeling. Heating system shut down because of high limit. Cleaned and tested furnace and replaced faulty run capacitor. Reset heating system and tested three times.
Heating repair. Found furnace did not have power. Upon inspection found door switch to be intermittent. Shimmed door switch, added note to interior of furnace. Need to replace door switch on next service call. No charge per technician.
Commercial heating repair. Checked temperature around barn floor temperature @50*, before floor was running at 65* check boilers found both boilers missing power on one leg of a 3 phase system, let customer know to call Com Ed to check service transformer.
Commercial furnace repair. Check floor temperature 60* to 68* on most of floor. Found a leak on one zone. Found wire burnt at fuse. Going to replace all the other fuse on this boiler they are soft. Due to age and being in a barn the fuses are paper shell. 2nd boiler is working, fuses are soft due to age, tore apart when pulling them out, replaced all fuses in this boiler.
Furnace maintenance safety and combustion inspection, recommend lower merv rating filter.
Furnace maintenance. Reset furnace to factory specs for safe, efficient operation. Toilet repair.
Provide annual safety inspection and energy boosting AC tune up. AC unit tested and performing well for cool indoor temperatures.
Naperville water heater repair. Not getting as much hot water as she is use to, cleaned and flushed water heater.
Naperville Huntington Hills neighborhood plumbing repair. Toilet replaced and free plumbing checkup.
Huntington Hill furnace repair in Naperville. Replace furnace gas valve.
Naperville Huntington Hill neighborhood hot water heater. Replace 50 gallon gas Bradford White water heater.
Replace Huntington Hill neighborhood hot water heater in Naperville. 50 gallon gas Bradford White water heater. 10 year warranty.
Water heater replacement
Anthony inspected hot water heater. Determined it was caused by a bad thermocouple. Replaced thermocouple and tested water heater. Everything is working properly now. Thank you.