With our five star reputation and professional education and experience, it's no wonder that Downers Grove, IL chooses PDM as their plumber and heating and cooling expert.
Our Downers Grove plumbers and HVAC technicians are highly trained professionals with genuinely good hearts and great personalities. We can't wait to start the day! Need more convincing? Give us a try, and you'll see why! Call PDM for guaranteed service.
Receive a proven 136 year track record of keeping your Downers Grove home and business safe and comfortable! Your PDM Plumbing, Heating, Cooling service team offers professional analysis of your comfort needs and great advice to fit your lifestyle. For additional ease of mind, your PDM service is backed by a strong warranty. Enjoy the convenience of our financing options that make repairs, new equipment and accessories affordable. Give us a try, and you'll see why!
- Heating Service in Downers Grove, IL
- Air Conditioning Service in Downers Grove, IL
- Plumbing in Downers Grove, IL
- Drain Cleaning in Downers Grove, IL
- Back-Up Generator Installation in Downers Grove, IL
- Remodeling Service in Downers Grove, IL
- Indoor Air Quality Service in Downers Grove, IL
- Duct Cleaning in Downers Grove, IL
As homeowners ourselves, we take great care to treat your home or business like it was our own. Any mess made will be cleaned up so you can get back to doing what you love quickly without hassle.
We love being Downers Grove's plumber and heating and cooling technician! Our exceptional 136 year reputation is the foundation for our success. To schedule plumbing, furnace, boiler, air conditioning repair or replacement call a trusted partner today!
for Downers Grove, IL
Our Reviews by City
School plumbing repair. Pull old toilet and found offset closet collar under toilet. I believe old toilet is a 12” rough. They only make 10” rough toilets for Sloan flush valve today. So I replaced closet collar and set the toilet. Sloan valve is off. I angled it to make work. To correct this I had to shut off water and replace a galvanized nipple coming out of the wall replaced with longer size. Toilet is working and not leaking as of this date.
ESTIMATE TO INSTALL NEW WATER LINE TO DRINKING FOUNTAIN
ESTIMATE TO REPLACE COLD WATER LINE IN BOILER ROOM
ESTIMATE TO REPLACE 3" MAIN WATER FEED TO HEADER
ESTIMATE TO INSTALL NEW WATER LINE FROM BOILER ROOM TO DRINKING FOUNTAIN NEAR THE CAFETERIA
ESTIMATE TO REPLACE WATER LINE
Clean and inspect 2 AC units, replaced 2 UV Bulbs, replaced 2 16x25x4 filters
Clean and inspect 1st and 2nd floor A/C units
Sump pump repair. Found float for primary pump not activating, replaced pump, float and controller under warranty.
Sump pump repair. Adjusted floats to proper levels, main and backup sump pump were too close to the same turn-on point.
Replace main sump pump. Second pit. Readjusted floats on backup sump pump systems.
Furnace repair, found electrical fault and repaired. Furnace tune-up to improve efficiency and spot weak parts. Furnace humidifier replaced solenoid on newer Aprilaire humidifier.
Furnace maintenance, replace two filters 16x25x4, replace one #35 humidifier pad, talked about auto shut offs for water supply came to the conclusion they cost to much, toilet handle was fine just needed tightening
Low water pressure service. Low flow due to dirty screen on water main.
Replaced toilet with an American Standard Town Square. Tested and hauled away old toilet.
ESTIMATE TO REPLACE EXISTING ROOF MOUNTED AIR CONDITIONING UNIT WHICH SERVES THE SCHOOL GYM
Bathroom plumbing remodel. Removed lav sink, 2nd floor, install replacement sink, chrome faucet and bone sink.
Furnace repair. Furnace board keeps losing power. Cleaned and tested furnace. Found power coming in and transformer all good. Replaced faulty relay board and pressure switch and air filter. Furnace is heating properly now.
Brookeridge home bathroom plumbing repair. Replace customer supplied toilet, replace emergency shut off stop for toilet, recommend replacing sink and faucet.
Drain repair. Replace cast iron Sanitary tee with PVC San tee on sewer line exiting home.
ESTIMATE TO INSTALL WATER TREATMENT SYSTEM
Air conditioning repair. Low voltage for 2nd floor ac wired backwards, switched wires around, test unit for safe operation.
Air conditioning repair. Found electrical faulty. Replace 40+5 capacitor on 1st floor ac unit. Test for safe operation. AC is cooling now.
Plumbing repair. Take water sample and provide estimate of work that needs to be done. Water filtration, bathroom remodel.
Air conditioning repair. No air conditioner call. Found condenser fan motor bad. Replaced with new motor and capacitor. AC is cooling now.