Leave Your Keys With Our New Lenox, IL HVAC & Plumbing Pros
For 138 years, PDM Plumbing, Heating & Cooling has been taking care of the great people of New Lenox, IL and all of their HVAC or plumbing needs. It's not often a company can claim over a century of experience; with that experience also comes the integrity to back up all of the work we do.
You can't benefit from a company that's just "go, go, go" all the time, cutting corners to save time and resources. You want a company that has stood the test of time not by doing things the "new" way, but by holding to old-school standards of quality and service.
Quick Plumbing Service Along With Heating & Cooling Emergency Repair In A Few Hours!
Choosing PDM brings all that experience and dedication to bear for all of your air conditioning, plumbing, heating and indoor air quality needs New Lenox, including:
Exceptional HVAC & Plumbing Service, Performed By Exceptional People
You want a contractor you can rely on. That's where we come in. Our entire process revolves around doing trustworthy, dependable work, carried out by the best of the best. All of our technicians have been through rigorous background checks and substance abuse testing. They are well-trained and certified in the work they do. You won't have to worry about anything; we take care of all the work and you'll hardly even know we were there.
Faithfully Serving The People Of New Lenox, IL
Our customers are important to us. Their opinion of us means more than anything. Which is why we're proud to show off the reviews we've received over the years. Take a look below to see what some of your New Lenox neighbors have to say about what PDM brings to the table. Then, to schedule your plumbing, heating or air conditioning service, message us online or call 815-726-6264 !
Plumbers can find water leaks in walls using the following methods:
- A visual inspection
- Using a moisture meter
- Using an infrared camera
Plumbers can typically find leaks through walls with visual inspection methods and tracing where the plumbing connections lead. If a plumber is unable to detect a leak with traditional methods, they can also utilize sound capturing devices and other technology to find the leak. Call us today to get your water leak detected.
It costs around $250-$900 to repair a water heater in New Lenox, IL. The cost of the repair will depend on the particular issue with your water heater and the severity level of the repair. Tank leaks are one of the most expensive hot water heater repairs, especially if the tank leak is severe. In some cases, having a tank leak repaired may outweigh replacing your water heater if it is reaching the end of its service life. To get your water heater repaired, contact PDM Plumbing, Heating & Cooling today.
Your home HVAC system may be running but not cooling your home because:
- Your air filters are dirty or clogged
- Your condensate drain line is clogged
- Your thermostat is set to the wrong setting
Some HVAC issues are a result of a lack of simple maintenance, such as replacing your air filters. However, your HVAC unit may be running but not cooling because there is a broken component within your system. To get your HVAC system repaired, contact us today.
A few reasons you may need to replace your home heating and air conditioning system are:
- Your HVAC unit is more than 10 years old and requires multiple repairs
- The cost to repair your HVAC is more than half the cost to replace it
- Your energy bills have increased drastically
Although replacing a heating and air conditioning system can be expensive, it saves you money in the long run. As HVAC systems become older and less efficient, they cost you more on energy and repair costs. To get your HVAC unit replaced, contact us today.
for New Lenox, IL
Our Reviews by City
ESTIMATE FOR NEW A/C.
Furnace maintenance, clean out all drain ports found a white cotton like substance blocking flue drain
PUMP & CLEAN OUT GREASE TRAPS / PITS
REPLACE ODOR HOGS
Replace leaking 40 gallon natural gas water heater.
Water pipe leak. Repair leak on 3/4” propress union on booster heater to wash machine. Material used in notes.
ESTIMATE TO REPLACE SEWER LINE
Piping repair. Install new 8” pvc plug with Teflon tape and a steel band around FIP adpt, to stop adpt from expanding. Material used in notes.
Medical plumbing repair. Replace checks on eyewash station in room 2354. No valves for this eyewash so I left stops in place cut brass st 90 in half remove both st 90 and repipe eyewash so there are 2- ball valves and spring loaded check valves before mixing valve so the cold does not cross over to cold Room#2470 SPD soiled room install check valves for mixing valve. Note this eyewash needs parts hospital is ordering the parts for this checks are in and working. Replace checks on eyewash stations, devices are working as of this date. Cold water would not shut down all the way, going to cut st on mixing valve and leave stops in place then add valves and spring loaded checks and relocate mixing valve to work in location Install spring checks in clean core#3 . Set mixing valve, all is good.
ESTIMATE TO INSTALL NEW WATER MAIN ON 5TH & 6TH FLOORS
Installed 40 gallon Bradford White gas water heater. Tested of safe operation, remove/recycle old water and clean work area.
Medical center kitchen plumbing repair. Repair broken waste line for disposal for dishwasher.
New commercial water main piping for remodeling work.
COMMERCIAL HOT WATER HEATER PK COMPACT TUBE BUNDLE REPLACEMENT
ESTIMATE TO REPLACE NON WORKING LOW FLOW PRESSURE REDUCING VALVE (PRV) #4 HOT LOW FLOW IN SOUTH MECHANICAL ROOM
COMMERCIAL WATER TREATMENT ESTIMATE TO INSTALL CUSTOMER SUPPLIED SANIPUR SYSTEM
This is a written report of work preformed on Friday Saturday and Sunday. Install chemical supplied to sanitize system-of the cold water and hot water and hot water return on the six floor building 7 and flushed system clean remove all stops and full flush into 5 gallon pals clean screens on mixing valve . Note some floor rooms have leaks that need repair Room# 6701 check valve return line 6702 cold water line 90 before valve, 6703 3/4” 90 on hot line and 1/2” 90 in wall behind room cabinets sink on hot water return line ,6706 3/4” and 1/2” line close to tee so tee will be replaced also and 1- 1/2” 90 behind cabinets sink hot water return line. Monday and Tuesday Chlorinate 5-7 area same as above pump in and flush system next day all stops blower out and showers with toilets . Wednesday Thursday and Friday repair leaks on 6th floor noted above all repairs have been made and system has been turned off each night and turned back on the next day to see if system lost pressure do to lea
Service furnace, clean sensor. Change out filter.
Pulled toilet to rod branch line.
Replaced pressure switch. Changed customer supplied furnace filter and water pad for humidifier.
Replaced transformer and thermostat on North furnace, middle furnace thermostat was also not working. Weak battery’s.
Kitchen drain cleaning. Rod kitchen sink. Flush drain and clean up.
Kitchen faucet repair. Tighten kitchen sink handle.
Medical center plumbing service. Kitchen dish area Pre rinse sprayer on pot sink was crossing over hot into the cold turning the cold water hot in bathrooms. Install spring checks under this faucet to stop the cross over. There are 3 eyewash stations in PACU that are crossing over. I shut water down and drain lines remove swing checks and install spring checks to stop water from crossing over into cold water side. One room had to add valves because house valves leaked.
Toilet drain cleaning. Pulled toilet to rod but wasn’t getting very far, used camera and realized I wasn’t making the turn to go outside of the foundation. Took apart piping in basement where the ejector ties into 4” cast and got my rod through that opening. Pulled back a lot of roots. Line is open.