Old Fashion New Lenox, IL HVAC & Plumbing Service
It's easy to overlook how important longevity can be for a New Lenox plumbing, heating & cooling contracting business. But every year, every job, every satisfied customer makes us better.
It is hard to benefit from a company that's just "go, go, go" all the time, cutting corners to save time and resources. If you want a company that has stood the test of time not by doing things the "new" way, but by holding to old-school standards of quality craftsmanship try PDM.
We don't just serve the New Lenox community - we're a part of it.
As a good neighbor people continue to trust PDM to take care of their business and home like it was our own. At PDM Plumbing, Heating & Cooling Since 1885, we're committed to doing things the old fashioned way in a new world - with passion, with professionalism and with dedication to being the best.
Quick Plumbing Service Along With Heating & Cooling Emergency Repair In A Few Hours!
Exceptional HVAC & Plumbing Service, Performed By Exceptional People.
You want a contractor you can rely on. That's where we come in. Our entire process revolves around doing trustworthy, dependable work, carried out by the best of the best. All of our technicians have been through rigorous background checks and substance abuse testing. They are well-trained and certified in the work they do. You won't have to worry about anything; we take care of all the work and you'll hardly even know we were there.
Faithfully Serving The People Of New Lenox, IL For 138 Years.
Our customers are important to us. Their opinion of us means more than anything. Which is why we're proud to show off the reviews we've received over the years. Take a look below to see what some of your New Lenox neighbors have to say about what PDM brings to the table. Then, to schedule your plumbing, heating or air conditioning service, message us online or call 815-726-6264 !
Plumbers can find water leaks in walls using the following methods:
- A visual inspection
- Using a moisture meter
- Using an infrared camera
Plumbers can typically find leaks through walls with visual inspection methods and tracing where the plumbing connections lead. If a plumber is unable to detect a leak with traditional methods, they can also utilize sound capturing devices and other technology to find the leak. Call us today to get your water leak detected.
It costs around $250-$900 to repair a water heater in New Lenox, IL. The cost of the repair will depend on the particular issue with your water heater and the severity level of the repair. Tank leaks are one of the most expensive hot water heater repairs, especially if the tank leak is severe. In some cases, having a tank leak repaired may outweigh replacing your water heater if it is reaching the end of its service life. To get your water heater repaired, contact PDM Plumbing, Heating & Cooling today.
Your home HVAC system may be running but not cooling your home because:
- Your air filters are dirty or clogged
- Your condensate drain line is clogged
- Your thermostat is set to the wrong setting
Some HVAC issues are a result of a lack of simple maintenance, such as replacing your air filters. However, your HVAC unit may be running but not cooling because there is a broken component within your system. To get your HVAC system repaired, contact us today.
A few reasons you may need to replace your home heating and air conditioning system are:
- Your HVAC unit is more than 10 years old and requires multiple repairs
- The cost to repair your HVAC is more than half the cost to replace it
- Your energy bills have increased drastically
Although replacing a heating and air conditioning system can be expensive, it saves you money in the long run. As HVAC systems become older and less efficient, they cost you more on energy and repair costs. To get your HVAC unit replaced, contact us today.
for New Lenox, IL
Our Reviews by City
5/16/2023 Demo all old pipes and drain pans from old system , demo old cabinets that are being replaced, go to shop make up sides out white aluminum facia material for drain under cabinet so water won’t splash out and sit on other side of raised lip on floor drain assembly and pick up material at shop for re work of pipes. 5/17/2023 Install sch 80 grate in floor drain. And route 2- 1” pvc drains through cabinets over to where pop and ice machine are being installed have to wait for the two pieces of equipment to to set in place to finish tie in. 5/18/2023 After counter top was installed run drains over to hole in counter and up through hole in the back.
ESTIMATE TO PUMP AND CLEAN LIFT STATION
ESTIMATE TO PUMP AND CLEAN LIFT STATION
ESTIMATE TO FLUSH AND TEST THERMAL EXPANSION TANKS , AND CHECK WATER PRESSURE REDUCING VALVES (PRV)
RPZ water backflow preventer repair. Rebuild backflow with complete rubber rebuild kit 1st,2nd check and relief kit. Backflow Device passed test afterwards filling out paper work someone flush a toilet upstairs causing a pressure drop on water supply relief opened on fire system and would not reset. Having Dave look to see if new relief assembly or if device has to be replace it is over 30 years old.
PO to come later she is on vacation this week. Work performed on 9/6/2023 1- repair 2” copper hot water line in room 5217. 2-room 6131 repair leak on mixing valve manifold 3/4” braze joint. Pull apart and replace st.90 on leak. Q Material in notes.
Annual water backflow preventer test to certify RPZ operation. File paperwork with city per state code. 7 RPZ Devices tested
ESTIMATE FOR PREVENTATIVE MAINTENANCE
Reconnected power wiring to door switch on furnace. Fixed wiring for control board. Washed outdoor units. Checked freon levels and tested.
Drain cleaning. Ran rod out 100’ four times with no luck. Camera would only go 17’ and everything was under water. Needs estimate to dig up and replace sewer.
Installed new ejector pump with float control.
Service A/C for season
Replaced 1-1/2” clean water ejector pump
Water leaked into furnace, inspect furnace and ac refrigerant levels
Go pick up materials and go to hospital, look at leak in Rm# 5107,5108 measure up section to be cut out and be replaced 2 1/2” copper cold main had a leak. Go down and prefab section to keep shut down to a minimum down time , Have Nick let staff water was getting shut down . Cut line made repair and bleed air out out system and turned back on , Nick let staff know water was back on. Put fiberglass insulation back on pipe with zeston 90. Material used in notes.
Cleaned and serviced condensing unit. Unit was extremely dirty with cottonwood. Had to burn it out before doing the wash out. Tested capacitor, contactor, fan motor amperage and compressor amperage. Capacitor tested below acceptable range and was replaced. Everything else tested in accurate working condition. Checked the 410a refrigerant levels. They were also in accurate efficiency range. Customer renewed maintenance program.
Clean and inspect AC unit, replace cap and start cap
Leak from kitchen sink basket strainer
2023 RPZ ESTIMATE
2023 RPZ ESTIMATE
Cleaned and serviced condensing unit. Tested capacitor, contactor, fan motor amperage and compressor amperage. Capacitor tested extremely low along the compressor side, and was replaced with a new 45/5 capacitor. Everything else tested in accurate working condition. Checked R22 refrigerant levels. Customers coil was below freezing temperatures. Added 1-1/2 lbs of R22 to bring temperatures up abouve freezing and to achieve accurate efficiency.
ESTIMATE TO REPLACE 2 TON CONDENSING UNIT
ESTIMATE FOR NEW A/C
Found chain from handle to flush valve cylinder had come off, could not find anything wrong with chain, reconnect and crimped clip to ensure this doesn’t happen again.
AC repair. Low on refrigerant. Recharge A/C system, blew out clogged condensate drain. Will work on energy efficient AC unit replacement estimate.