Old Fashioned HVAC New Lenox Service.
It's easy to overlook how important longevity can be for HVAC New Lenox IL. But every year, every job, every satisfied customer makes us better.
It is hard to benefit from heating and cooling companies in New Lenox that's just "go, go, go" all the time, cutting corners to save time and resources. If you want a company that has stood the test of time not by doing things the "new" way, but by holding to old-school standards of quality craftsmanship, try PDM Since 1885.
We Don't Just Serve The New Lenox Community - We're A Part Of It.
As a good old fashioned neighbor, people continue to trust PDM to take care of their business and home like it was our own. At PDM Plumbing, Heating & Cooling Since 1885, we're committed to doing things the right way - with passion, with professionalism and with dedication to being the best.
Quick New Lenox Plumbers For Emergency Repair!
Choosing PDM plumbers in New Lenox, IL brings all that experience and dedication to bear for any plumbing service.
Plumber New Lenox Ode to Pipes Restored. New Lenox water woes, Clogged drains and overflowing woes. But fear not, friend, there's help at hand, A plumber's skill, a saving band. We'll be there, To banish blockages, with nary a care. From kitchen sinks to bathroom woes, He'll make those pipes sing, like a sweet bread. So if your gurgle turns to groan, And water backs up, like a mournful tone, Call a PDM plumber, don't delay, He'll fix your leaks, come what may.
Exceptional HVAC & Plumbing Service, Performed By Exceptional People.
You want a contractor you can rely on. That's where we come in. Our entire process revolves around doing trustworthy, dependable work, carried out by the best of the best.
All of our plumbers and HVAC technicians have been through rigorous background checks and substance abuse testing. They are well-trained and certified in the work they do. You won't have to worry about anything; we take care of all the work and you'll hardly even know we were there.
Faithfully Serving The People Of New Lenox For 138 Years.
Our customers are important to us. Their opinion of us means more than anything. Which is why we're proud to show off the reviews we've received over the years. Take a look what our reviews have to say about what PDM brings to the table. Then, to schedule your plumbing, heating or air conditioning service, message us online or call 815-726-6264 !
Plumbers can find water leaks in walls using the following methods:
- A visual inspection
- Using a moisture meter
- Using an infrared camera
Plumbers can typically find leaks through walls with visual inspection methods and tracing where the plumbing connections lead. If a plumber is unable to detect a leak with traditional methods, they can also utilize sound capturing devices and other technology to find the leak. Call us today to get your water leak detected.
It costs around $250-$900 to repair a water heater in New Lenox, IL. The cost of the repair will depend on the particular issue with your water heater and the severity level of the repair. Tank leaks are one of the most expensive hot water heater repairs, especially if the tank leak is severe. In some cases, having a tank leak repaired may outweigh replacing your water heater if it is reaching the end of its service life. To get your water heater repaired, contact PDM Plumbing, Heating & Cooling today.
Your home HVAC system may be running but not cooling your home because:
- Your air filters are dirty or clogged
- Your condensate drain line is clogged
- Your thermostat is set to the wrong setting
Some HVAC issues are a result of a lack of simple maintenance, such as replacing your air filters. However, your HVAC unit may be running but not cooling because there is a broken component within your system. To get your HVAC system repaired, contact us today.
A few reasons you may need to replace your home heating and air conditioning system are:
- Your HVAC unit is more than 10 years old and requires multiple repairs
- The cost to repair your HVAC is more than half the cost to replace it
- Your energy bills have increased drastically
Although replacing a heating and air conditioning system can be expensive, it saves you money in the long run. As HVAC systems become older and less efficient, they cost you more on energy and repair costs. To get your HVAC unit replaced, contact us today.
for New Lenox, IL
Our Reviews by City
ESTIMATE TO REPLACE TUB / SHOWER UNIT WITH SHOWER BASE
Provide estimate to excavate sewer and replace 2 whole home humidifiers
Commercial water heater repair. Found unit leaking in ceiling of suite 265 and leaking 24” safety pan. Install 19 gallon AO Smith electric water heater converted to 277 volts single phase.
Replace sump pump. Mid-Range, added protection with upgraded sump pump.
ESTIMATE TO REPLACE BLADDER IN WESSELS TANK
Kitchen drain pipe repair. Pipe from kitchen sink was detached and there was a crack on a san tee in the wall under the sink. Repiped from traps into the basement. Sewer line is full of grease. Power rod drain to clear blockage. Drain is flowing now.
Main pump in pair of pumps wasn’t working. Dropped in another pair of pumps and was having the same issue. Figured it was air lock. Took apart the check valves and rubber couplings that come assembled with the pump and re piped with quiet checks which was successful. Work done under warranty.
Medical center plumbing repair.
WATER BACKFLOW DEVICE TESTING AND ESTIMATE TO REPAIR 6" RPZ
Cleaned and serviced furnace. Tested flame sensor, pressure switches, hsi, fan motor amperage and capacitor, inducer motor amperage and gas valve voltage. Everything is in adequate working condition. Replaced furnace filter that customer provided. Humidifier filter is in good shape still. Customer has one more visit remaining for spring.performed free inspection.
Cleaned and serviced furnace. Tested flame sensor, pressure switches, hsi, fan motor amperage and capacitor, inducer motor amperage, and gas valve voltage. Replaced flame sensor and hsi due to corrosion. Replaced humidifier filter that customer provided. Cleaned out exhaust pipe and drains. Customer renewed maintenance program. One visit is being used today, and they will have one visit remaining for 2024 season.
Medical Center water softener repair. I did the repair on softener #2 and refilled softener and put it through regeneration. Replace fittings and nipples on softener #1. These where about to let go sent photos to Joe, also took photos and photos of submittals for a revised quote for replacement of these units.
ESTIMATE TO PUMP AND CLEAN GREASE TRAP AND BASINS
Cleaned and diagnosed furnace. Tested flame sensor, pressure switches, hsi, fan motor amperage, inducer motor amperage. Being a 96% furnace cleaned out all the drain lines and drain tubing connected to the inducer motor and collector box and flu. Replaced flame sensor and hsi due to corrosion. Customer renewed maintenance program. One visit is being used today and they will have one remaining for condensing unit in 2024 season. Replaced furnace filter that customer provided. (20x25x4). Performed free inspections.
Drain cleaning. Rodded outside downspout southwest corner, found roots. Cleared blockage.
Reduced pressure zone RPZ water backflow annual test. Test and certified 5 backflow’s file paperwork with the city per state code. 1-6”backflow 2-4”backflow’s 2-3/4” backflow’s Note 6” backflow of. Fire system failed e mailed Dave information to get Katie a quote.
ESTIMATE TO REPAIR BROKEN MAIN SEWER LINE
Installed relay, per factory specifications.
ESTIMATE TO PUMP AND CLEAN LIFT STATION
Provided estimate to certify and test RPZ's for 2023.
11/11/2023 1- replace B&G recirculating pump in ceiling in suite 265 also and 3 valve on line with drain valve so return can be bleed of all air so it is it air locked. Also install check on return so cold water will not back up in return line . Remove mixing valve on all exam room sink for flushing of system next week left the ones under bathroom sink’s behind porcelain skirt. These bathrooms are used by the public. 11/18/2023 chlorinate suite 265 have chemical guy test water for right mix leave in for 6 hrs and flush system , water test of system to be done by others. Material used in notes.
Toilet repair. Float on fill valve in toilet was set too high so fill valve was continuously running and sending water down the overflow, adjusted float which solved the issue. Customer elected to keep those parts as long as they’re working. Performed clean and check on furnace to ensure safe, efficient operation.
Commercial furnace repair. Go to job look at furnace, found transformer blown. Replaced transformer on furnace, tested and is working as it should.
Found distorted gasket in hot side dielectric union, replaced and tested, no leak at this time.
Medical plumbing repair. Remove section of 2” pvc and 4” pvc pipe and fittings that were leaking, replace with new fittings and pipe. Clean up room and have EVS do a deep cleaning to put room back in service.