With our five star reputation and professional education and experience, it’s no wonder that Elwood, IL chooses PDM as their plumber and heating and cooling expert.
Read below what your Elwood, IL neighbors say about our plumbers and HVAC team. You’ll like what you see!
for Elwood, IL
Our Reviews by City
Diana - Elwood, IL
Anthony is a great person and he explains everything that is wrong and fixes them. I would never call any other Company to work around our house. Thank you for all your help.
Mike - Elwood, IL
Anthony was very professional and knowledgeable. He fixed our issue quickly.
Reputable people that stand behind their work
Marie - Elwood, IL
I use PDM for all my plumbing needs. “Pete” was just at my home to repair a toilet I had a problem with 2 months ago. Not only did he correct the issue, PDM stood by their reputation of outstanding service and did not charge me again to fix the problem to my satisfaction. Thank you PDM !!!
Great Service, was patient and explained all the details so I could understand the extent of the problem.
Kathy - Elwood, IL
Simply put AnthonyFloyed is an amazing asset to your organization.
Barbara - Elwood, IL
Chris was extremely thorough and explained every thing he did to resolve our problem. I feel very confident with him and this company.
Barbara - Elwood, IL
Chris was awesome. He answered all my questions, did a thorough cleaning of furnace, and was so pleasant to talk to. My first experience with PDM and I am so glad I found them. He was honest and promptly arrived within the time frame. He even corrected some issues done by previous serviceman from another company. If you need any heating or cooling work done, call this company and keep your fingers crossed that you get to meet Chris.
Pm and repair Weil McLain ultra boiler
Clean and check trane furnace
Replace shower valve and moen trim kit
AC repair. Air movement fault in the voltage absorption system. Safety controls not responding to commands. Restore system and test cooling operation.
Air conditioning repair. Replace blower motor and capacitor. Air conditioning maintenance clean and check and rest to factory specs. Tested AC system, operating properly.
Commercial drain cleaning. Rod outdoor field tile. Tested operation.
REPLACED 40 GALLON WATER HEATER. TESTED.
Clean and inspect 5 air conditioning units
REMOVED TOILET. REPLACED FLANGE. RESET AND TESTED.
HOME FURNACE MAINTENANCE. FOUND FAULTY HIGH LIMIT SWITCH. RESET SYSTEM TO FACTORY SPECS FOR SAFE, EFFICIENT OPERATION. TEST WHOLE HOME HUMIDIFIER. REPLACE WATER SHUT OFF FOR HUMIDIFIER AND #10 HUMIDFIER PAD. CLEANED ORIFICE ON WATER LINE TO HUMIDIFIER. TEST FOR SAFE OPERATION.
A no heat turned out to be a very dirty 13 year old Standard furnace with several issues. First, the air filter was very dirty, causing the unit to cycle on and off with the high limit switch. This overheating cycling caused the switch to fail. The drain assembly inside the furnace was also partially plugged up. Gave the unit a thorough clean and check. Also, repaired the humidifier and replaced the pad. Checked pumps and water heater and advised client to replace both.
Repair shower valve cartridge and repair koler toliet fill valve
Repair hot water heater vapor sensor
Replace spray head on kitchen faucet
Clean and check on a newer Goodman furnace. All values within manufacturers specifications.
Replaced a 75 gallon hot water heater that was vented with 50 feet of double wall steel pipe with a power vent unit that vents with 4 inch PVC pipe.
Repair to water heater thermocouple
Elwood commercial plumbing faucet repair. Test and clean up.
Elwood commercial HVAC maintenance. Clean and test four AC systems. Equipment very dirty. Reset to factory specs for safe, efficient operation. Clean up work area.
Inspect furnace for basement water damage. Clean, test for safe operation. Found A-Coil is rusty. System working ok. Clean up work area.
Elwood plumbing repair. Replace outside faucet. Add access panel and ball valve emergency shut off valve. Test operation and clean up.
Furnace repair. No heat. Fault in the low voltage distribution system. Change thermostat battery. Heat is flowing again...