Reliable Toilet Or Urinal Repair Every Time.
As the technology of commercial restroom fixtures become more complicated, water saving faucet, toilet and urinal repair become more complex. PDM Plumbers love tough commercial toilet or urinal repair challenges.
Sloan and Zurn flush valves are a common flushometer we are experienced at repairing and installing. Here are some common toilet or urinal flush valve FAQ.
8 Toilet Or Urinal Flush Valve Troubleshooting FAQ Tips 2023.
TOILET OR URINAL HAS A POOR FLUSH.
Do you have enough water to adequately siphon the fixture? Do you have the wrong part installed or a faulty water saving kit?
FLUSH VALVE RUNS.
If a Diaphragm flushometer: Replace the Solenoid assembly. Rinse a clogged diaphragm bypass orifice. The diaphragm assembly may be faulty. Or a low water pressure problem. If a Piston type flushometers: Debris is blocking the bypass; clean, rinse the orifice. Replace the piston assembly because a faulty relief valve seat. Or low water drop causes the valve to run.
FLUSH LASTS TOO LONG.
Your diaphragm by-pass orifice may be clogged or you have a relief valve problem. If cleaning does not work, replace the diaphragm. If water line pressure is not sufficient to force the relief valve to seat, shut off all control stops until the pressure has been restored, then open stops again.
SHORT FLUSH. FLUSH VALVE SHUTS OFF IMMEDIATELY.
Your diaphragm assembly is worn. Yo have a damaged handle assembly. A water saver diaphragm assembly may to be replaced or relief valve with the correct flush volume. If you’d like professional help, call PDM.
FLUSH VALVE DOES NOT FLUSH.
Is the control stop or the main valve supply closed? Or maybe the handle assembly or relief valve is worn out?
Water splashing out of a fixture or from a leaky flush handle can be a safety and health risk. Your control stop may be open more than necessary or a wrong diaphragm assembly was installed.
Flushometer can leak in a number of places including: Flushometer Cover Leak, Control Stop Leak, Tailpiece Leak, Spud Flange Coupling Leak, Vacuum Breaker Leak, Handle Leak.
Experienced, Quick Commercial Toilet or Urinal Plumbing Repair In Joliet SW Chicago Suburbs.
Give PDM a chance to prove our value. We’ll quickly identify and fix the urinal or toilet problem to local standards.
At PDM we believe integrity, character, and generosity trumps everything else.
- We follow through on our promises.
- We offer quality products that are expertly manufactured from the finest materials.
- We never make excuses or shift the blame to others.
- We have a proven track record and the experience to get the job done safely and quickly.
Let PDM Plumbing Since 1885 Get You Back To Normal Fast.
We have a proven 138 year track record and the experience to get the commercial plumbing job done right. Guaranteed. Call PDM for a quick knowledgeable, professional plumber in the Joliet and SW Chicago suburbs.
Schedule an appointment today of call 815-726-6264.Commercial Plumbing for Local Churches and Schools: Learn More » « Plumbing Services in Plainfield, Illinois From The Oldest Plumber