With our five star reputation and professional education and experience, it’s no wonder that New Lenox, IL chooses PDM as their plumber and heating and cooling expert.
Read below what your New Lenox, IL neighbors say about our plumbers and HVAC team. You’ll like what you see!
for New Lenox, IL
Our Reviews by City
Always Excellent Service
Patricia - New Lenox, IL
I've been a PDM customer for around 15 years now and I have always been very satisfied with their prompt response and the quality of their service. They genuinely care about their customers. My recent problem was a leaking hot water pipe and after fixing it, Chris noted the whole pipe should probably be replaced since it was very corroded. I did schedule another appointment so he could do the recommended replacement. I appreciated him bringing the problem to my attention.
Response from PDM Plumbing, Heating, Cooling Since 1885:
Thank you Patricia for expecting the best from us. And thank you Patricia for your service review. We all are happy to have kept you comfortable over the years and look forward to our next visit. Stay well Patricia. Your PDM Comfort Team.
Great service and I will use PDM again
Lisa - New Lenox, IL
Great service and quick too!
Slowiak - New Lenox, IL
I had a sump pump fail and had inches of water in my entire basement. Pete came out, assessed the situation and fixed it in a short amount of time. I couldn't have asked for better service!
Dan - New Lenox, IL
Service man paid attention to details, was very knowledgable and even corrected some mistakes the installer made. I highly recommend PDM.
Great service and very honest.
Jankowski - New Lenox, IL
Pete Wilson was our technician and he was extremely professional and honest. He completed the job in a timely manner and cleaned up when he was done. Thank you very much PDM!!
Quick response time. Professional assetment of problem. Very courteous repair man.
Kendall Hackman - New Lenox, IL
This is the second time that we have used PDM's service. We would confidently recommend PDM to family and friends. Always fast and courteous response to issues. Highly satified with all associations with PDM. They are our go to service for all our plumbing issues.
Thomas - New Lenox, IL
Technician arrived at the scheduled appointment time. He was very knowledgeable about my furnace and gave helpful advice on its future maintenance. A very good experience!
Mike - New Lenox, IL
Mark - New Lenox, IL
Chris was outstanding. Went above and beyond. Left everything cleaner than when he got here.
Charles - New Lenox, IL
Chris was very knowledgeable and gave great service.
This is not a bill this is a summary of work performed on 1/10/2021. Repair 2 1/2â€ copper leak in ceiling 2nd floor surgery nurses front desk.Notes have material list for todayâ€™s job.
Hospital drain cleaning. Rodded drain line from waiting room washroom in suite 430, cleared line at this time. Clean work area.
Commercial RPZ backflow device test. This is not a bill it is a description of work performed on 1/6/2021, rebuild 1/2 inch backflow device in RM 4460.1 DI closet. RPZ device is repaired and tested. Material used is in notes.
Water piping repair. Re-pipe section of 1/2 copper pipe in crawl space.
Water piping repair. Repiped 1/2 inch copper water line to kitchen sink. Tested and cleaned up.
Work Done: Work Suggested:
Hospital plumbing repair. Vacuum out Little pits, take pictures and get a material list for repairs
Furnace maintenance. Clean and check furnace, replaced faulty hot surface igniter, fs, also replaced furnace drain line.
Replace outside lawn faucet
Repair cartridge on Delta kitchen faucet, repair flapper on Kohler bathroom toilet, clean garbage disposer
Air conditioning annual maintenance. Adjust, calibrate and reset the finer points to squeeze every ounce of efficiency and comfort from the furnace and outdoor AC unit system. Check Thermostat temp accuracy. Activate and Test all HVAC Controls for proper operation, programming, communication, and accuracy. AC system is operating well.
Commercial pipe leak. Protected hallway, drained system and repaired 1-1/2" copper heating line. Bled air, insulated pipe and cleaned area.
Clean commercial lift station for surgery center. Pump and clean basin using high pressure jetting. Clean and test operation.
Installed ejector pump and repiped sump discharge
MEDICAL CENTER EMERGENCY SERVICE: REPAIR 2" COPPER WATER LINE FOR LEAK
Checked tub/shower backup
Replaced ejector pump
Clean and check on an older Bryan furnace that has had the exchanger replaced. Everything checks out to manufacturers specs. Also checked the sump and ejector pumps as well as, the water heater. Humidifier pad good to go for the season.
Clean and check on an older Bryan furnace. Checked sump pump, battery backup system and ejector pump. Everything looks great and ready for the winter season.
Install 1 inch RPZ backflow device