With our five star reputation and professional education and experience, it’s no wonder that Minooka, IL chooses PDM as their plumber and heating and cooling expert.
Read below what your Minooka, IL neighbors say about our plumbers and HVAC team. You’ll like what you see!
for Minooka, IL
Our Reviews by City
Clean inspect furnace
Leigh - Minooka, IL
Tech provided efficient timely service
Boucher - Minooka, IL
Very satisfied with service
Hogan - Minooka, IL
Always the best service
buza - Minooka, IL
Clean and check furnace. Renewed plan. Gave estimates on replacing inducer fan noisy, replacing furnace, and replacing water softener.
Install Rinnai tankless water heater, model RU199IN, serial mhba - 094698. Test operation and clean work area.
Bathroom faucet repair. Replace 2 piece Kohler shower cartridge. Test operation.
Plumbing repair. Re-pipe under kitchen sink, hook up new Moen garbage disposal 3/4 hp. Hook up dishwasher the correct way according to code. Inspect water softener the camshaft and clock timer connector plastic piece is broken, recommend replacing water softener. Faucet repair. Replace cartridge on master bath left side sink, inspect all connections for leaks found none at this time.
Customer supplied valve, we were out last week to trouble shoot.
Water heater repair. 239-48796-01, diagnostic on (2) 50 gallon power vent water heaters , tech support confirmed gas valve, customer will order part, LP.
Another great day at PDM! Thanks to all our great customers, techs, and office staff.
Leaving my house to go to work at PDM Plumbing Heating and Cooling! Should be another great day!
Water heater replacement
Replace 40 gallon propane water heater made by state
Commercial AC maintenance. Tune two ac systems and reset to factory specs for safe, efficient operation. AC systems are cooling properly.
REPLACED OUTSIDE LAWN FAUCET AT FRONT OF THE HOUSE. TESTED OPERATION AND FOUND EVERYTHING WORKING FINE.
Clean and inspect Ac
Cleared floor drain blockage
REPAIR PIPE LEAK AND REPLACE SUMP PUMP WITH INDUSTRIAL GRADE PUMP. TEST FOR SAFE OPERATION.
Check sewer system and replace sump pump
Repaired running toilet
Replaced on dryer venting system that was improperly installed from day one. Drilled through the face brick and installed steel venting system up to code. Covered old holes and caulked with urethane caulk.
Clean and check on a Carrier roof top unit that has had the heat exchanger system rebuilt. Changed the filters and checked the thermostat.
Replaced the blower motor and capacitor on an older Carrier furnace and tested. Good to go for the season.
Clean and check carrier furnace
Clean and check on an older American standard furnace. Running okay but several components are testing poorly.
Clean and check on a Carrier furnace. All values good, but the fan motor tested poorly. Also checked the sump pump and ejector pump, okay.