With our five star reputation and professional education and experience, it’s no wonder that Frankfort, IL chooses PDM as their plumber and heating and cooling expert.
Read below what your Frankfort, IL neighbors say about our plumbers and HVAC team. You’ll like what you see!
for Frankfort, IL
Our Reviews by City
Great Service, Terrible Price
Jim - Frankfort, IL
Pete did a fine job. Less than 15 minutes on site. Invoice does not show individual pricing; just a quantity of 1 for Dispatch fee, tank lever handle replacement, $20 off coupon and a member savings of $45.65. Total cost $184.35. I have dealt with PD&M for over 35 years and recommended them to others on numerous occasions.First time I am totally disappointed. Good thingI am a member. if not the cost would have been $250.00....
Excellent service at a great price!
Vicky - Frankfort, IL
Anthony, our service technician (plumber) was very professional, friendly and extremely knowledgeable. He took care of the leaky situation quickly and efficiently.
Karl - Frankfort, IL
Very professional service !
Mr Steve - Frankfort, IL
Very courteous and professional phone staff with great follow through and my technician, Anthony was very competent, professional and timely in his work on my project. I would definitely recommend them to others.
Farquhar - Frankfort, IL
Pete Was professional courteous and efficient with his work. He did the work neatly safely and courteously. I would recommend PDM to others especially as quickly as they responded and performed the work. I felt pricing was a little higher than I had expected.
Excellent advice and troubleshooting over the phone from your technician on a rainey Sunday night regarding my ejector pump malfunction, followed up b
Steve - Frankfort, IL
Jim - Frankfort, IL
Day 1, replaced battery on backup sump. Worked find. Day 2, sump died, replaced with new system. 1 hour later alarm for system usage. Day 3, adjusted float level. System back on. Overall, I ask myself was something done (with no malice) that caused the sump to die on day 1. Still think the world of Rudy and will continue to use PDM.
As always, great service
Eighner - Frankfort, IL
Brian - Frankfort, IL
Technicians always give great tips on maintaining my furnace and AC unit.
Order two sets for the water heater. Two flame sensors two gaskets and two spark rods.to be billed We need to return and install a new set when the parts come in.
Replaced 1/2â€ boiler valve with 1/2â€ ball valve and 1/2â€boiler valve. To be billed.
Checked plumbing connections to dishwasher, does not appear to be plumbing related. Suggest contacting appliance repair company
Toilet repair. Replace broken Kohler toilet handle. Test operation.
School water piping repair. Shut down main water and drain system. Remove section of 1 inch copper that was leaking. Install new copper piping. Re-sweat fittings and turn water system back. No leaks. Job is complete. This is not an invoice this is just scope of work that was done on Tuesday, January 5, 2021
Replace hot and cold angle stops on basement kitchen sink, disconnect ice maker line and add a extension to the cold side of basement kitchen faucet, parts in photo
Drain cleaning. Rod lavatory drain second floor hall bath, sink closest to door. Tested operation and cleaned up.
Furnace repair. Found three light diagnostic - inducer fan on when I arrived. Board needs to be replaced. Return Monday morning with new board. Replace control board with hot surface igniter and tested. 12/21/20
Furnace repair. Tested inducer system, found motor pulling .5 amps, rated at 1.0 amps. Vacuum pressures low. See notes.
Kitchen sink leak
Replace outside lawn water faucets. Test operation.
Replace drinking fountain. Remove and recycle old drinking fountain. Install Elkay barrier free filtered water cooler with bottle filling station. Start up and test operation. Cold, fresh water is now flowing.
Replaced roman tub faucet
Install pair of pumps battery back up system and repair water heater
Install new pro series sump pump with alarm and 4 yr manufacturers warrenty
Test backfow devices
Made repairs to sloan automatic toliet valve in elementary school
Had to replace the control board on an older American. standard furnace. The unit would cycle just fine but would go it lockout when the call for heat ended. Replaced board and tested three times!
Clean and check on two American Standard furnaces. Replaced the media air filters, humidifier pads and sheeted the return drops with 26 gauge steel.
Clean and check on two older Carrier furnaces. Replaced filters and customer supplied UV lamp. Also checked sump pump and ejector pump. Water heaters look good also.
Frankfort AC checkup. Inspect HVAC system top to bottom, clean and reset to factory specs. AC cooling well.
Frankfort sump pump running constantly. pump was tested and was running properly. Inspected Trane HVAC system and found burnt wiring. Replace wiring and clean HVAC system. All working well now. Clean up work area.
Frankfort air conditioning replacement. Disconnect old AC system and recycle refrigerant and old unit. Install new energy efficient Amana 3.5 ton AC system and coil. Start-up and test operation. AC running perfectly. Clean up work area.
Frankfort air conditioning. Clean and check on two Bryant original air conditioning systems. Both checked out average for their age. Pressures slightly high but reasonable.